Have Your Furnace Inspected Yearly
Only about 30% of a home's heating system is reviewed by the local gas provider if they are called out for a seasonal start-up. This leaves 70% of the review of the heating system to the homeowner or possibly to untrained personnel.
Floor furnaces can be dirty, prohibiting combustion air needed to allow for proper flame causing soot and the potential for aldehydes and allowing CO into the home.
If the property you are considering has a floor furnace be sure to ask the home inspector to fully review the vent system under the house.
Forced air heating units atop roofs may have loose or leaking gas lines A homeowner may not realize there is a problem even though there may be higher gas bills. Roof mounted units may have damaged supports or other related problems.
Forced air heating units mounted in closets can be another potential for problems. Units today are required to be secured and mounted over the return air hole and tightly sealed. If not properly placed and caulked this will interfere with the flow of natural combustion air affecting the flame and cause venting gases, or carbon monoxide, to flow into the home via the ducts. Heater compartment (or closet) doors need to be sealed and should latch tightly if the return air register is within 10 feet of the door. Upper and lower combustion air openings located inside the closet should be clear of debris and obstructions, allowing combustion air to flow. Obstructions such as insulation can inhibit proper air flow causing the heater to burn improperly. Missing fire blocks below the lower combustion air vents can allow the venting process to reverse causing , again, the heater to burn improperly and vent gases and aldehydes into the home through the ducting system.
Wall furnaces have a high potential for cracks in the heat exchangers. Ask your home inspector to review closely with a mirror and flashlight. The home inspector cannot always see a crack in a heat exchanger but may be able to locate those that are visible or suspect. The unit may need to be cleaned before lighting the pilot. You may also wish to ask the home inspector to review carefully the venting system in the attic crawl spaces when the inspector checks this area.
Watch out for the home which has been occupied by the same owner for years. The heating system may not meet today's safety standards and would typically, after and inspection by the gas supplier, be "red-tagged" until replaced or repaired. This could be uncomfortable for a new homeowner if the weather is extremely cold and the repair cost is out-of-pocket.
The Gas Company or provider usually offer a no-charge safety inspection to their customers. It is highly recommended to have this performed regardless if you had the home inspected. A diligent inspection of the heating system, venting system, and a careful review of heat exchangers can possibly save a life or prevent loss by fire.
Remember, even if you have a home inspection get the furnace cleaned, serviced and certified by a Professional Contractor. The heat exchanger is hidden and a home inspector can not see the complete heat exchanger unless it is taken apart or special equiptment is used. Have the furnace cleaned and checked on a regular basis.
Suggest regularly changing or cleaning filters to maintain proper airflow to the furnace. Dirty filters can slow the air and reduce efficiency.
Independent Home Inspections, LLC
Serving Columbus and Central Ohio
Rick A. Harrington
(614) 768-1190 fax
Thermal Imaging (Infrared)
Indoor Air Quality & Mold Sampling
Radon and pest inspections
Contact us for all your Columbus Ohio Home Inspection needs.